Your best choice for Furnace & Air Conditioning Repair in Jersey City, NJ
Interstate Air Conditioning & Heating is your best choice for repair, installation, and service in homes and buildings just like yours in the New Jersey area. We take special pride in the craftsmen we train and employ–a fact you’ll see in their reviews below. It’s also noticeable immediately in the attitude and integrity our technicians bring to your job site.
Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Interstate Air Conditioning & Heating stands behind the work we do as well as comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for Furnace & Air Conditioning Repair in Jersey City NJ.
Call us today at (908) 497-7793!
for Jersey City, NJ
Easy to book!
Ayal - Jersey City, NJ
I appreciate their responsiveness regarding our HVAC issue that was submitted through email. Great company to work with.
Prompt and low prices
G - Jersey City, NJ
Thanks again, guys! The company customer service personal reached out to me right after I first contacted them and was able to schedule someone to come in the next morning. He showed up on time and fixed our problem efficiently
Responsive and knowledgeable company!
Millie - Jersey City, NJ
This company is our forever-go-to contact for all HVAC issues in the future. They did an excellent job on all the 3 times we've called them.
Diana - Jersey City, NJ
He was a very professional expert. He identified the problems and got the team to work on it in the evening. We had a lot of questions and he explained everything from bit to pieces. Professional and good!
They were fully equipped
Houston - Jersey City, NJ
Our AC broke down and we had to suffer for it for a whole week. Interstate did an amazing job in repairing our AC without giving us any pressure. Everything went so smooth.
justin - Jersey City, NJ
We were explained in detailed regarding the indoor and outdoor component of the HVAC system even the high side and the low side of the air conditioner. Friendly team, great explanation!
Great and easy to deal with!
Lisa - Jersey City, NJ
They made sure that their client (my company) was happy with their service, gave us tips and tricks to lengthen the lifespan of the air conditioner system and equipped with the knowledge that we needed!
Jukey - Jersey City, NJ
Great customer service, very professional and very reasonable price was given to us.
Brown - Jersey City, NJ
Great team! Neat and a thorough job was done. Thanks guys.
Air Conditioner's PCB
Wesley - Jersey City, NJ
As complicated as it was for us, they fixed the circuit super well!
HVAC Unit had a refrigerant leak and a leak check was needed. Pressurized the circuit and found leak coming from the equalizer tube where the flare nut attaches to the suction line. removed the flare fitting and brazed the equalizer tube straight to the suction line. replaced the liquid line drier as well. tested for further leaks at 350 psi of nitrogen, found an additional leak by the compressor Repaired leak, evacuated and set into a deep 342 micron vacuum. recharged with 11.1 lbs of R-22. operating pressures: 66.9 psi low, 216 psi head. 21.2 RLA out of 26.0 RLA
performed residential condenser replacement. Removed the old condenser and liquid line drier and installed 1 new condenser and drier along with a site glass. pulled vacuum to 500 microns added refrigerant and started up the system.